Based on the edition of NFPA 58, the third edition of the Fire Safety under the NFPA 58 (, , , and editions). 5. Vent Assembly. 6. PVC Elbow; 3/4” x 90°. Regulator Venting According to NFPA (NFPA 58, edition). The point of discharge from the required. These amended regulations shall be effective on February 1, (a) NFPA 58, Liquefied Petroleum Gas Code, edition excluding.
|Published:||8 September 2015|
|PDF File Size:||4.66 Mb|
|ePub File Size:||4.41 Mb|
Installation of containers on roofs of buildings shall be prohibited.
The first sentence of Section 6. All incurred costs for additional testing required by the Division shall be the responsibility of the owner.
Specifications of the type of container, container history if known, material specifications and calculations, and condition of the container shall be submitted to the Division by the nfpa 58 2011 seeking nfpa 58 2011 "Special Classification Permit".
The Division shall inspect the container for approval. If the Division has concerns about the integrity or condition of the container, additional nondestructive tests such as hydrostatic testing, ultrasonic metal thickness testing or any other testing as determined necessary by the Division.
All nfpa 58 2011 costs of testing and evaluations shall be the responsibility of the owner.
The Division will approve or nfpa 58 2011 the proposed container. Approval by the Division shall be obtained before the container is set or filled with LP Gas.
Type K copper tubing without joints below grade may be used in exterior LP Gas piping systems only. Provide and install all pneumatic nfpa 58 2011 and tubing as required for remote shutdown nfpa 58 2011 as required by NFPA Provide and fabricate nitrogen bottle rack on site to secure gas source for automatic shut down systems.
- NFPA Liquefied Petroleum Gas Code
- NFPA Liquefied Petroleum Gas Code,
- DAR File No. (Rule R) UT Bull (11/15/)
- NFPA Pamphlet 58 (2011 Upgrades)
- Notice of Proposed Rule
- Looking for other ways to read this?
Nfpa 58 2011 any pipe supports or new concrete stations to support pipe if required after piping reconfiguration.
Remove old or abandoned piping from systems that may have been modified in the past.
Minnesota Legislature - Office of the Revisor of Statutes
New rules include cathodic protection for underground tanks guards against corrosion to preserve structural integrity. In most areas of the country, soil characteristics are detrimental to the integrity of steel containers buried underground.
Corrosion creates pits or holes nfpa 58 2011 left alone or ignored can lead to leaks, releasing propane into the ground.